The Sensazone electronic management system controls water flow with solenoid valves and is designed to control up to three 2W 2/2 bi-stable (latching) solenoid valves per washroom area sensor. If motion is detected by the infrared sensor the valves open to supply water to building zones, as required (e.g. washrooms or kitchens). If no movement is detected for a pre-set period (configurable to 15 or 30 minutes), water supply is cut off.
A Sensazone Light & Fan Shut-Off Connection Module is available as an optional system specification to control the operation of lighting and extractor fans, as required.
The power supply to the lighting will activate when Sensazone detects that the washroom is occupied and when ambient light falls below a level configurable by the user. Power will continue to be supplied for either a 0, 15 or 30 minute period, depending on preference.
The Sensazone Light & Fan Shut-Off Connection Module can be connected to any sensor in the system. If required the cable can be extended up to a maximum length of 100 metres with 1.5mm2 CSA cable.
Extractor fan operation can also be configured; users have the option of using Sensazone to control the fan run-on time, or using the fan unit’s own timer facility (dependent on model selected).
Sensazone can be configured either manually or via the hand-held remote control Infrared Configuration Unit (ICU) which is available separately as an optional extra and makes setting the Sensazone system quick and easy.
Here is a selection of documents, designed to ease specification and installation:
Here is video content illustrating the technical application of this product:
BIM objects are available for download from the NBS National BIM Library, in both Revit and IFC formats.
Parts only warranty (no labour) for equipment purchased in the United Kingdom, Ireland, Isle of Man and the Channel Islands. Components of the unit which are proven to be faulty or defective in manufacture will be exchanged or repaired.
1 Year from Date of Manufacture
3 Years from Date of Installation
To register and qualify for Extended Warranty cover, the Cistermiser product must be correctly installed with the Commissioning Checklist fully completed as itemised in the Installation Guide (included with the product), to demonstrate compliance with the product installation instructions.
Each Commissioning Checklist activity should be dated and additional warranty details provided to enable registration: product serial number, installation date, installation site address and the installer’s name and contact details.
Extended Warranty can be registered online (via the Warranty section of this website) or by completing and returning the Commissioning Checklist from the Installation Guide (included with the product) to this address: Cistermiser Ltd, Unit 1, Woodley Park Estate, 59-69 Reading Road, Woodley, Berkshire RG5 3AN.
"I've been a volume customer of Cistermiser for many years. Good products and excellent support."
"Your company is great - the parts, the service, the delivery, the clarity, the simplicity - all brilliant - definitely a score of 5! Many thanks."
"Many thanks, your product (Combimate) has proven itself time and time again over the years."
"Thanks to all, you have some fantastic staff who took the time and effort to help us out."
"I installed my Combimate about six weeks ago, and it's been brilliant. Water tastes better and I'm pretty sure I've seen a reduced build-up of limescale. Many thanks to you and to everyone there. I'm really so pleased how much better my water is!”